On Wed, Jul 1, 2009 at 11:09 AM, Randall<email@example.com> wrote:
>> Check your local code. B This is allowed by the NEC, and it requires
>> either a double pole breaker, or the two handles of single pole
>> breakers to be mechanically tied together (So half the 240 outlet
>> isn't hot.); however, many local jurisdictions don't allow it, or
>> allow it only under limited circumstances.
> I missed something here, David. B Are you saying that split-phase is
> in some places? B Or is it linking two single-pole breakers (which after
> is what is inside a double pole breaker) that is not allowed?
Split phase. Some places also prohibit more than one receptacle on a
Support Team.Net http://www.team.net/donate.html
Shop-talk mailing list